Average-value three-phase AC voltage to DC voltage converter with fixed power loss
Simscape / Electrical / Semiconductors & Converters / Converters
The Average-Value Rectifier (Three-Phase) block models an average-value, full-wave, six-pulse rectifier. It converts instantaneous three-phase AC voltages to DC voltage and DC power demand to three-phase AC power demand. The corresponding AC power demand is equal to the sum of the fixed power loss and the DC power demand.
You can use the Average-Value Rectifier (Three-Phase) block only as a six-pulse rectifier. You cannot combine two Average-Value Rectifier blocks to represent a twelve-pulse rectifier.
The figure shows the equivalent circuit for the rectifier as a full-wave, six-pulse rectifier. The Average-Value Rectifier (Three-Phase) block does not yield the harmonics that are typically associated with the detailed representation, however, because it performs an average-value power conversion.
The voltages are defined by:
va, vb, vc are the respective AC phase voltages.
vref is the DC offset on the AC
side. In a balanced AC power system with no DC bias,
VRMS is the RMS AC line-line voltage.
vDC is the voltage difference between the positive and negative terminals of the rectifier.
is the vDC /VRMS ratio for a full-wave, six-pulse rectifier.
vp, vn are the voltages at the positive and negative terminals of the rectifier.
The resistance, power, and currents are defined by
VRated is the rated AC voltage that you specify on the block mask.
Pfixed is the fixed power loss that you specify on the block mask.
Rfixed is the fixed per-phase series resistance in an equivalent wye-connected load.
ip, in are the currents flowing into the positive and negative terminals of the rectifier.
PDC is the power output on
the DC side. PDC has a minimum
RAC is the per-phase series resistance in an equivalent wye-connected load.
ia, ib, ic are the respective AC phase currents flowing into the rectifier.
Rated AC voltage— Rated AC voltage
Rated voltage of the AC system.
Fixed power loss— Fixed power loss
Minimum power drawn on the AC side at rated AC voltage. When the instantaneous AC voltage is equal to the value you specify for the Rated AC voltage, the AC power demand equals the value you specify for the Fixed power loss plus DC power demand.
Average-Value Chopper | Average-Value DC-DC Converter | Average-Value Inverter (Three-Phase) | Bidirectional DC-DC Converter | Boost Converter | Buck Converter | Buck-Boost Converter | Converter (Three-Phase) | Rectifier (Three-Phase) | Three-Level Converter (Three-Phase)